Mixed-use office and apartment building just outside of downtown Milwaukee. The building features 120 studio and one-bedroom apartments, a 2,250 retail stall, and seven floors of offices.
~~Outdoor Swimming Pool~~~~Provide MSDS sheets for all pool chemicals~~~~Provide and maintain required first aid supplies~~~~Maintain all electrical equipment and lighting~~~~Pool equipment shall be properly located, installed and maintained and repaired as necessary. Test the Safety Vacuum Release System (SVRS) as per manufacturer's recommendations. Provide a test log for the inspector to review. / DHS 172.33(1)(e) /~~~~The flow through each skimmer shall be adjusted as often as necessary to maintain a vigorous skimming action at each skimmer. Adjust the west skimmer to provide vigorous skimming action. / DHS 172.11(2)(a) /
~~Outdoor Swimming Pool~~~~Skimmers, skimmer weirs, and overflow gutters and drains shall be maintained so that they are clean and shall be repaired or replaced as needed. Replace expired Virginia Graham Baker Act drain covers and/or equalizer covers with appropriate replacements and provide the inspector with supporting documentation regarding the replacement.The main drain cover is due for replacement. / DHS 172.11(2)(b) /
Fire Suppression r